SP2-40K-N Mersen Type 2 1P Neutral Replacement Cartridge
Available at LED Controls the Mersen Type 2 surge protector replacement cartridge SP2-40K-N has 1 Pole and a working voltage of Neutral, a maximum continuous voltage limit of 265 volts and a nominal discharge current of 20Ka. These units should be replaced once the indicator on the front shows red.
These cartridges are easily replaceable as you only have to pull on the old cartridge to remove it and push in the replacement. p>
|Product Image||For Illustration Purposes Only|
|Number of Poles||1 pole|
|Maximum Continuous Voltage||265V|
|Nominal Discharge Current||20Ka|
|Product Lead Time||Standard Delivery 7-10 Days|
Protection system of coordinated stages: Type 1, 2 and 3 SPDs
The SPDs of a surge protection system must be able to withstand the discharged current and provide a Ures level (residua l voltage) lower than the Ue peak voltage that the equipment can withstand. Most of the times it is not possible to achieve this with just one SPD, especially because the intensity of the surge is not known, and because of the induction of overvoltages when conductors exceed 10m.
The optimal system of protection is the 3-STEP approach, in which successive stages are combined in the performance of high discharge capacity devices and devices with an optimal voltage protection level (low). This is addressed by the definition of "Types" or "Classes" of SPDs according to the type of transient pulses to which each protected zone in the installation is subject to.